Just a quick note to say thanks for the advice on the replacement of the Mother board. We attended a week ago and all went smoothly, no problems since touch wood! You provide a great service, you have an excellent range of products and deliver on the double. Here in Cork, Ireland it can be difficult to get certain brands and parts of fire alarm systems. You have been a great help. So thank you.
|Published (Last):||14 April 2006|
|PDF File Size:||2.58 Mb|
|ePub File Size:||4.27 Mb|
|Price:||Free* [*Free Regsitration Required]|
Failure to comply may result in the system initiating a Fire or Fault signal Detector installation must comply with local regulations. User Configuration Settings Access to the configuration settings is through the back plate of the Detector Head. If in Auto condition has been removed. Wiring Diagram For connection of a single conventional Detector to a zone: Note 1?
Prism Targeting Mode Apply power to the Detector. The faster the flash the nearer terial and confirm t5. Alignment Mode Mode Switch to the middle position. Slowly adjust a thumbwheel in one direction and observe the flashing? Operating Mode On exiting alignment mode the Detector will perform an internal calibration check.
Do not block the beam whilst this internal calibration takes place. The Amber LED will flash once a second, for up to sixty seconds, and then go out. In If the internal calibration check completes satisfactory, the Detector will now be in normal 7. System Testing After successful installation and alignment the System will require testUsing a non-reflective object, quickly cover the entire prism s.
The Detector will indicate a fault within 10 seconds by activating the FATaking note of the threshold selected during installation, select obscuration mark on filter to Place the filter over the receiver optics Top of Detector Head opposite end to the status indication LED? A Compensation Fault can be cleared by cleaning the Reflector and Detector lenses using a dry lint-free cloth, and then re-aults can be avoided by periodic cleaning of the Reflector ation limit is reached.
These cookies will be stored in your browser only with your consent. You also have the option to opt-out of these cookies. But opting out of some of these cookies may have an effect on your browsing experience. Necessary cookies are absolutely essential for the website to function properly. This category only includes cookies that ensures basic functionalities and security features of the website. These cookies do not store any personal information.
Any cookies that may not be particularly necessary for the website to function and is used specifically to collect user personal data via analytics, ads, other embedded contents are termed as non-necessary cookies.
Please add products before saving :. Back Guardar presupuesto. Then send it to yourself, or a friend, with a link to retrieve it at any time. From Name. Have a look at this Shopping Cart sent by a friend via Hommax Sistemas. Send Cart Email. Your cart email sent successfully :.
FireRay® 5000 beam detector, 50-100 m
Fireray 100 RV with four prisms